You can configure your WAGO-TO-PASS so that the transmitted signals are stored in Databoom.
Create a device in Databoom
Before proceeding with the configuration of your WAGO, you must create a device in Databoom that can connect to the physical device.
In Devices section, clik on "Add device" and then select the type "WAGO-TO-PASS" among the available types. Once the creation is completed, it is important to edit its token. From the edit device screen, click on the "Edit" button, next to the token field.
The new token must be as follows:
wago<SERIAL NUMBER WAGO-TO-PASS>
The serial number is a 5 digits number written on the device (the 0 at the beggining of the code, if present, is not to be considered).
WARNING! Editing the token is fundamental to connect your device, if not done properly, the data will not be recorded.
The fundamental parameters you need to configure in order to connect Databoom to your WAGO-TO-PASS are Script (value), the route where the server receives the values and Script (logger), the route where the server receives the logs
Their values must match, respectively, to:
value<10 CHARACTERS API KEY PORTION>
logger<10 CHARACTERS API KEY PORTION>
The last 10 characters can be copied easily by clicking the appropriate icon in your user's profile, next to the API key field.
The other parameters to configure in the Addresses tab are:
- Host address, Databoom dedicated server address, topass.databoom.com
- Host port, the port where the server is listening, 8080
- Script version, select the option FW 2.33
In the Speciality functions -> Repeat Times tab, it is possible to set the value of Web interval that is the time between each communication.
Once the procedure has been completed, Databoom starts to record data from the WAGO. To examine your data and have a correct representation, follow the instructions in Edit/validation of a signal.